Per the user guide
The below commands help you change the alerts on a UPS Network Management Card 2 using SSH , cannot be done via Web Interface
cfgpower -all ( Show all applicable power parameters for this UPS. )
cfgpower -l ( 97–106 Set the low transfer point, in VAC. )
cfgpower -h (127–136 Set the high transfer point, in VAC.)
cfgpower –ov (100 | 120 | 110 |) – Set the outlet voltage, in VAC.
cfgpower -s Normal | Reduced | Low ) – Set the sensitivity, using one of the three arguments.
cfgpower -bu (127 | 130 | 133 |136 | 139 | 142 |145 | 148 ) – Set the bypass upper voltage in VAC; when the voltage rises above this value, the device goes into bypass. )
cfgpower -bl (086 | 088 | 090 | 092 | 094 | 096 | 098 | 100 ) – Set the bypass lower voltage in VAC; when the voltage drops below this value, the device goes into bypass. )